New LoadMatch® Thermostats Offer Exceptional Control
> E-mail Newsletters
For HVAC pros designing and installing Taco LoadMatch® Hydronic Systems,
we’ve just introduced a line of LoadMatch Thermostats
for exceptional control of your heat pump or fan coil LoadMatch Systems.
Designed specifically for LoadMatch Systems, these all-in-one controls are pre-programmed and require little or no additional configuration
to make your system ready to operate.
You'll find them versatile, too. All LoadMatch Thermostats are available in BACnet, Echelon-Lontalk and non-communicating versions for use with virtually any building system
. In addition, you can order fan coil models with relative humidity (RH) sensors to provide local dehumidification with reheat capability, for the ultimate in comfort and efficiency
Taco LoadMatch Thermostat features include:
- Preprogrammed and LoadMatch ready
- All-in-one control
- Familiar thermostat look and interface
- Large backlit display and clear function buttons
- Available in stand-alone and network versions
- Hinged design with removable terminal blocks for easy installation
As a Taco Green product, the LoadMatch System is ideal for sustainable design or green building projects
and can help your projects qualify for LEED Certification by the U.S. Green Building Council.
Get more information on LoadMatch thermostats.
Get more information on the Taco LoadMatch System.
More Files, More News at www.TACO-HVAC.com
We added more than 400 files
to the Taco Document Library
last month alone. That's just one way we try to give you the product, application and technical support you need to build your business. Some others are:
Take a look. Get the most from www.taco-hvac.com
HVAC Pros Ask…Question: What are the ZC and ZR terminals on the SR506 Switching Relay and how are they used?
ZC/ZR terminals on the Switching Relay
board go to ZC/ZR terminals on the triple aquastat with ZC/ZR terminals, using minimum 14 gauge wires. These terminals will prioritize domestic water coil. When there is a demand for heat from the thermostat, ZR becomes hot, sending 120 volts to the triple aquastat. When the boiler temperature rises above the minimum temperature setting (typically 140°), ZC becomes hot, sending 120 volts to the SR board and powering the relay for the circulators. To recap, the circulators cannot run until the boiler is keeping up with demand.
Remember, at any time and from any Internet connection
, you can get complete information on Taco products, support, news and the latest information, at www.TACO-HVAC.com
Thanks for your interest.